8 OUT OF 10 NON-HEALTHCARE FACILITIES HAVE NOT INSPECTED THEIR DAMPERS*
Do you know what the code is for damper testing and damper repair?
NFPA 80 states that:
19.4.1 Each damper shall be tested and inspected 1 year after installation
126.96.36.199. The test and inspection frequency shall then be every 4 years except in hospitals where the frequency shall then be every six years
NFPA 105 states that:
6.5.1 Smoke dampers for dedicated and non-dedicated smoke control systems shall be inspected and tested in accordance with NFPA 92A, Standard for Smoke-Control Systems Utilizing Barriers and Pressure Differences
6.5.2 Each damper shall be tested and inspected one year after installation. The test and inspection frequency shall then be every 4 years, except in hospitals where the frequency shall be every 6 years.
Check out our list of top 10 deficiencies within the healthcare arena.
NFPA Code has very specific, detailed inspection and reporting requirements.
To learn more about the testing requirements for fire damper testing, smoke damper testing and fire and smoke damper repair, please visit our website, www.LifeSafetyServices.com or contact LSS Life Safety Services directly, 1.888.675.4519.